email@example.com Derby Road, Derby DE73 6RU
8.30am to 6.30pm Monday to Friday
RICS Home Surveys Information Sheet - Homebuyers Surveys - Homebuyers Survey Fees - Building/ Structural Surveys
Typical 1900 terrace house
The bottom corner near the drain corner was fractured and leaning outwards on bothe elevation up to a height of about the tenth row of bricks. Movement considered to be due to historic drianage failure that had now been repaired.
Modern plastic drain running past the corner seen from the manhole
No fractures in the kichen which had been replastered about ten years ago
Undulating bricks at low level on an outhouse. No corresponding movement on the interior. Movement likely to be due to poor foundation construction or past mining movmement as the area is know for undergroud lime stone mines. Report from the coal board recommended as a precaution.
Approximately vertical fracture of the juncture of the outhosue with the rest of the structure. Probably due to thermal movment of a long south facing wall in the hot summer months. If the wall becomes too hot it expands beyond its elasticity and fractures. It can then never move back.
RICS Building Survey
Leicester Office: 51 Henley Road, Leicester, LE3 9RD Derby Office: 34 Queen Street Derby DE1 3DS Coventry Office: The Apex, 2 Sheriffs Orchard, Coventry CV1 3PP Birmingham Office: 22 High Street Sutton Coldfield Birmingham B72 1UX Notingham Office: Courtyard Business Centre, 41a Southwold Drive, Nottingham NG8 1PA Sheffield Office: 16 High Street, Sheffield, S43 3UX